Sterile Environment Technologies practices proper procedures to Decontaminate your Data Center or similar mission critical indoor environment.
ISO 14644 Standards can be found through IEST, the Secretariat of ISO/TC209.
ASHRAE STANDARD: Particulate and Gaseous Contamination Guidelines for Data Centers
“It is incumbent on data center managers to do their part in maintaining hardware reliability by monitoring and controlling the dust and gaseous contamination in their data centers. Data centers must be kept clean to Class 8 of ISO 14644-1, Cleanrooms and Associated Controlled Environments—Part 1: Classification of Air Cleanliness
Sources of dust inside data centers should be reduced. Every effort should be made to filter out dust that has deliquescent relative humidity less than the maximum allowable relative humidity in the data center. The gaseous contamination should be within the modified severity level G1 of ANSI/ISA-71.04-1985, Environmental Conditions for Process Measurement and Control Systems: Airborne Contaminants (ISA 1985), which meets:
1. A copper reactivity rate of less than 300 Å/month and
2. A silver reactivity rate of less than 300 Å/month.
Above Referenced From: ASHRAE – Particulate and Gaseous Contamination Guidelines for Data Centers.
Free 13-Page PDF can be found here.
General Data Center Cabling/Space Standards
Telcordia GR-3160, “NEBS Requirements for Telecommunications Data Center Equipment and Spaces” (available for purchase, primarily used by Telco’s)
ISO/IEC 24764, “Information technology – Generic cabling systems for data centres” (available for purchase, similar to the cabling content of TIA-942 but written for the international market)
ASHRAE TC9.9 and TGG publications are excellent guidelines.
ANSI/TIA-942-A is the Telecommunications Infrastructure Standard for Data Centers and was approved this year August_2012. There is also the ANSI/Bicsi-002_2011 Data Center Design and Implementation Best Practices that was approved in January 2011. Both documents are very helpful to Data Center Owners/Operators, Telcomm/IT Consultants and PMs along with telcomm/IT installers. Both Documents are for design/build/operation of physical
layer systems for data centers.
American National Standards Institute (ANSI) is the accrediting agency who recognizes TIA, Bicsi and many other technology associations for their “openness, balance, consensus and due process” when developing industry standards.
What is Federal Standard 209e for Data Centers?
The outmoded (replaced by ISO 14644) benchmark for optimum and safe operating levels is compared to Federal Standard 209e for Data Centers at 100,000 particles at .5 microns per cubic foot of air space. Optimum levels for temperature should normally be 70 to 72 degrees Fahrenheit, with humidity levels at 50%.
Please note: equipment manufacturers have varying optimum operating levels.
Federal Standard 209E has been replaced with ISO Standard 14644. The first subsection in ISO 14644 (ISO STND. 14644-1) has some unique changes from the old Federal Standard – however they are very similar. This standard is now in effect for critical environments (Cleanrooms, Data Centers, etc.) worldwide. Some companies have been successful with the federal Standard 209E, and may not have switched over yet. It is important for these companies to know the main differences are easy to implement and may not be a costly change.
The main differences between Federal Standard 209E and ISO 14644-1 (Testing Standards) are:
- ISO Establishes 0.1um as the “Standard” Diameter
- ISO Creates 3 New Cleanliness Classes-
- 2 “Cleaner” classes (ISO class 1 and ISO class 2) than Federal Standard 209E
- 1 “Dirtier” Class (ISO Class 9) which is allows more particulate than Fed Standard 209E class 100,000
- Allows for discarding of “Outliers” – Federal Standard 209E did not.
International Standards for Cleanrooms and Critical Environments
International Cleanroom Standards:
ISO/TC209 has proposed ten (10) documents which will make up the cleanroom standards. These documents are in their final voting stages and can be legally used in trade. The tables and sections below outline the first seven of these documents in order.
ISO-14644-1 Classification of Air Cleanliness
Cleanliness class designations and quantity have changed from FS209E (see Table 1). Along with the obvious change to metric measure of air volume, ISO 14644-1 adds three additional classes.
(Table 1) Airborne Particulate Cleanliness Classes (same as table above)
|Class||Number of Particles per Cubic Meter by Micrometer Size|
|0.1 um||0.2 um||0.3 um||0.5 um||1 um||5 um|
(Table 2) Comparing FED STD 209E to the new ISO 14644-1.
Airborne Particulate Cleanliness Class Comparison
FED STD 209E
|ISO-14644-2 Cleanroom Testing for Compliance
This document determines the type and frequency of testing required to conform with the standard.
|Test Parameter||Class||Maximum Time Interval||Test Procedure|
|Particle Count Test||< or = ISO 5||6 Months||ISO 14644-1 Annex A|
|> ISO 5||12 Months|
|Air Pressure Difference||All Classes||12 Months||ISO 14644-1 Annex B5|
|Airflow||All Classes||12 Months||ISO 14644-1 Annex B4|
|Test Parameter||Class||Maximum Time Interval||Test Procedure|
|Installed Filter Leakage||All Classes||24 Months||ISO 14644-3 Annex B6|
|Containment Leakage||All Classes||24 Months||ISO 14644-3 Annex B4|
|Recovery||All Classes||24 Months||ISO 14644-3 Annex B13|
|Airflow Visualization||All Classes||24 Months||ISO 14644-3 Annex B7|
ISO-14644-4 Cleanroom Design & Construction
This document will be a primer on the design and construction of cleanrooms. It will cover all aspects of the process from design development to startup and commissioning.
ISO-14644-5 Cleanroom Operations
This document will be an introduction on cleanroom operation. It will cover all aspects of the operation of a cleanroom including entry and exit procedures for equipment and personnel, education and training, cleanroom apparel, and facility issues such as maintenance, housekeeping, monitoring, system failure, etc.
ISO-14644-6 Terms, Definitions & Units
This document will provide a consistent reference for all terms, definitions and units discussed across all ISO cleanroom standards.
ISO-14644-7 Minienvironments & Isolators
This document will focus on specialized stand-alone clean spaces including their design, construction, and operations.